Now that this social science and technology is constantly developing, the environment is getting worse. With the harm caused by environmental pollution, people are paying more and more attention to environmental protection. ，垃圾随意乱丢，污水量逐渐增加，人们的环保意识也在上升，开始使用污水处理设备 ，但是长期使用后往往会出现问题，那么污水 处理设备不运作的原因是什么呢?有以下几种常见的情况。 Deforestation , random littering, the amount of sewage is gradually increasing, people's awareness of environmental protection is also rising, and the use of sewage treatment equipment , but problems often occur after long-term use, so what is the reason for the sewage treatment equipment does not work? Yes There are several common situations.
立体填料)。 1. The sewage treatment equipment can't produce water normally: Whether the communication pipelines contacting the oxidation pond, sedimentation pond, disinfection pond, and sludge pond are blocked (the blockage is generally the falling biofilm and the damaged elastic three-dimensional filler).
2. The aeration of the contact oxidation tank is uneven: check whether the outlet valve of the aeration fan is in the normal position and whether the aeration head is damaged.
营养(白糖、尿素等)。 3. The effect of the biofilm connection is not obvious: check whether the aeration in the contact oxidation tank is uniform, and whether the sludge from the secondary sedimentation tank is pumped to the tank. If the above conditions are normal, add the appropriate amount of nutrients (sugar, urea, etc.) to the tank . ).
彻底清除污泥)，消毒装置停运和长期对出水不进行消毒。 4. The quality of the effluent of the sewage treatment equipment is not up to the standard: the water intake is too large; the aeration in the oxidation tank is not uniform or the operation is suspended for a long time (the biofilm must be re-cultured at this time); the sludge in the sedimentation tank is excessive (the sludge must be completely removed) , The disinfection device is out of service and the effluent is not disinfected for a long time.
断路开关自动断开)。 5. Failure of automatic control of sewage treatment equipment: check whether the power of the automatic control cabinet is normal, and check whether the supporting lift pump and aeration fan are damaged (at this time, an excessive current can be formed, and the disconnect switch is automatically disconnected).
The above is the reason why the sewage treatment equipment does not work. I hope it will be helpful to you. 业解答。 If you still don't understand the question, please call Quanding Environmental Protection Sewage Treatment Equipment Company to answer your questions professionally .